How to hook up Shelly 2.5 on a 3-way switch?
It is not clear to me how you can use a SPST switch like Shelly’s, the to run a 3-way circuit. 3-way setups rely on SPDT switch. And if you have two SPDT-smart-switches to a 3-way circuit, you would have to mean both traveler plus, and download in both fields.
use this wiring, the load to perform a 3-way with a traditional smart switch and a “companion” by rezoning to one of the travellers, such as neutral and common for the store – allowing you to load a warm – /neutral – / – /travellers in the switch box and neutral – / – /travellers in the accompanying box. (Smart switch companions need only travelers+neutral.)
Released on Thu, 07 May 2020 13:50:43 +0000